You can change damper positions from the CCU or the Smart Node for testing purposes. If testing from the CCU you must have the CCU connected to its docking station for damper testing to work. Without a connection to the docking station the CCU will have no way to transmit or receive messages from the terminal zones.
Find the zone in the list that you are looking to test and slide the slider to the position you desire. It may take up to 2 minutes but you will see the damper move to the desired position.
You can also change the damper position from the Smart Node. To do this:
- Click the right button until the Outputs screen
- Click down to the desired output
- Click right to highlight the output signal
- Click up or down to change the value to the desired output
*Note - Damper1 and Damper2 are 75F Smart Dampers (also termed MAT dampers) and would be plugged into the RJ45 ports on the left of the Smart Node.