30 Minute Read; Includes 3 videos
The Smart Node is a highly versatile input/output (IO) controller. There are many applications that can be setup out of the box with minimal configuration options. The Smart Node can also be used for more custom sequences that are outside its typical terminal application profiles.
- Do not install devices in direct sunlight.
- Do not install devices on an exterior wall.
- Do not install devices near an heat producing equipment.
- Disconnect power before installing. Never connect or disconnect wiring with power applied.
- Do not run Wall Sensor harness next to line voltage.
- Install in accordance with all state and local codes.
- Do not mount the Smart Node directly on the bottom of duct work. This can cause a potential drip hazard to the electronics in the case of any condensation buildup.
- Mount the Smart Node between the angle encompassed by the 8 and 4 O'clock of the duct work.
- Accurate Temperature
- Accurate Humidity
- Wireless communication to Central Control Unit (CCU)
- Operating Environment: 0°F – 122°F
- Max power consumption: 3.5VA
- Each Analog Out is capable of 20mA max
Mounting the Smart Node
To Mount the 75F Smart Node, first identify the primary damper in the zone. If there is only one damper, that is the primary damper. If there are two, pick the most accessible damper as you will need access to the Smart Node. Using the provided hex key bolts, fix the Smart Node to the damper side bracket cage nuts until snug.
Installing a Wall Sensor
To install the Wall Sensor, drill a 1 inch hole saw. Determine where to ideally install the Wall Sensor. Also ensure the sensor will not be installed behind any objects such as picture frames, shelving units, equipment, etc. When these conditions are met, drill a 1 inch hole at desired location which is 5 feet off the ground. The desired location for drilling the point hole should be not lower than 4 feet 6 inches and not higher than 5 feet 6 inches if possible.
Installing a Local Interface Sensor
The Local Interface Sensor is an alternate sensor with local control. To install the Local Interface Sensor you will drill a 1-1/4 inch hole 5 feet from the floor. Plug the 4-Pin cable into the slot in the back of the mounting plate. Slide the Local Interface Sensor mounting plastic into the 1-1/4 inch hole. Tighten the toggle bolt to secure the mounting plate to the wall.
For other sensor options checkout these articles:
**For accurate performance ensure:
- There are no heat producing devices near to the sensors
- That the installation is not done on the exterior wall
- That the sensor is not exposed to strong drafts or direct sunlight
The Smart Node is an IO controller that is capable of controlling many unique applications. You will know what terminal profile you should be using based on the equipment you have. For wiring and specific terminal profile configuration please choose the link below.
Wall Sensor Harness
Both ends of the Wall Sensor harness are the same male connectors. Run one of the ends down the wall and feed through the 1 inch hole drilled previously. Plug into the Wall Sensor. Plug the other end into the RTS port on the Smart Node.
Local Interface Sensor
The 4 Pin cable will be secured to the Local Interface Sensor mounting plastics. When the Local Interface Sensor is snapped onto the mount the pins will make connection. The other end of the 4 pin cable will be plugged into the RS485 port on the Smart Node.
Powering the Smart Node
To power the smart node run your 18/2AWG bus line to the Power IN on the Smart Node. All devices with a shared transformer must be the same polarity. If you have another Smart Node that needs to be powered, daisy chain them from Power OUT to the next Power IN. Secure your cables so there is no excessive strain on any connections.
Connect the Smart Damper(s)
First connect the primary damper RJ45 lead to the Damper1 port on the Smart Node. Run the Cat5 extension cable from the Smart Node Damper2 port (Male end) to the RJ45 lead (Female end) on the secondary damper. Ensure all connections are tight and cables managed so no excess stress occurs on any connection.
Pair the Smart Node to a zone that has been preconfigured or create and configure a zone yourself through Setup > Floor Plan on the CCU.
Once power is supplied to the system and all Smart Nodes are displaying the default room.
- Disconnect the tablet from the CM and carry it with. Pairing will be performed using Bluetooth.
- On the Wall Sensor push the small “Pair” button for 2 seconds. This puts the Smart Node into advertising mode. Alternatively, you can press the right button on the Smart Node until you reach advertising mode.
On the tablet choose the zone you wish to pair and press “Pair Module.” Pairing process will start. If no zones are displayed you will need to add all floors and rooms before pairing. Choose the type of profile the Smart Node will be.
Select Smart Node Device Type.
Select the Terminal Profile the Smart Node will be controlling.
Follow the pairing steps on the Smart Node and press Pair.
The tablet will request a PIN. Enter the PIN displayed on the Smart Node in the zone you are pairing.
- Pairing process will take a few more seconds and then complete displaying Success on the screen. After a few more seconds the Smart Node will display the new zone name. The tablet will not display any zone data until it is reconnected to the CM where it will communicate over a 900 Mhz channel.